A》 If the column of water between the pump and the highest tap exceeds 15mts, the unit cannot be installed directly on the pump controller, but it has to be raised until the column of water between the unit and the highest tap does not exceed 15mts. I.E:If column of water is 20 mts. from the pump, the unit must be placed 5 mts highest than the pump controller.
The unit is equipped with a check valve to prevent the pipeline from losing pressure.
B》 No taps can be installed between the pump and the unit.
C》 The unit is pre-set by the Manufacturer at a restarting Pressure of 1.5bar. The pressure produced by the Pump must be normally 0.5bar higher than the pre-set pressure.
D》 Before pulling the unit before starting the pump controller, check that the pump is primed.
E》 It is advisable to connect the unit outlet to the system by means of a flexible hose.
F》Safety valve preventing water emission in case of diaphragm break
DO NOT TOUCH
G》 It is imperative to install the unit with the arrows in the upward position.
H》 The unit can be installed directly on the pump, or between the pump controller and the first tap.
Wiring diagram for connection of single-phase 220V pumps up to 1.1 Kw.
1.1Kw.through wiring diagram for connection of single-phase 220V pump on remote control switch.
Wiring diagram for connection of three phase 380 V motor pump controller through remote control switch.
1》The pump controller does not start .
2》The pump controller does not stop.
3》Intermittent pump working.
4》The Pump is jammed.
CAUSES DEPENDING ON THE UNIT
1》The electronic card is broken.
2》The flow detector is blocked in the upper position.
3》The reset button is blocked
4》 The pump controller does not provide sufficient pressure.
5》The pump provides a pressure which is lower than.
CAUSES NOT DEPENDING ON THE UNIT
3》Electric cables inverted(Line/motor).
4》Presence of leaks which are higher than the minimum flow 0.6 /min.
5》Presence of leaks which are lower than the minimum flow 0.6 /min
On the cover behind the terminal board and on the cover, a drawing shows how to make the connection properly. The cable used should have 6 mm min. and 9 mm max. outside diameter, In order to guarantee the water tight enclosure of the box, the four screws on its box must be tightly screwed
When the unit is connected to the electrical network, the green LED “power on” lights and yellow LED on “(pump in operation) indicates that the pump controller has been started.
The pump continues to work for a few seconds to fill the system in the pipe and reach the required pressure.
If this lapse is insufficient, the red led”Failure” lights, up. In this event.keep the Restart” button pressed and wait, with a tap opened,until the red led is off. Once released the button and closed the tap, the unit stops the pump controller at its maximum pressure.
The operation started was started, the unit is programmed to automatic control system execute all the pump level control functions. the unit recognizes the breakdown and the red led “Failure” lights up:at the same time a stop signal is sent to the pump to prevent damages caused by its working in the absence of water. Rectification of the failures that have caused the blockage, allows the system to be restarted by pressing the “Restart” button.
My name is Ravindra Singh a professional Technology, Blogger & Youtuber. After completion of my studies in utterprades, I moved to Ethiopia for my very first job, I am work Habesha Steel & Blog, At the beginning of my corporate career, I felt myself very Lucky that I got a white collar Job in such a big HSM where people dreams off to get in.
But I was innocent! In two years of corporate life, I got to know that I am not made for corporate kind of things, I feel very uncomfortable while doing a 4 to 5 job.
One question I always asks myself every day when I go to office – “How people of corporate can do same work on the daily basis without learning?” How they can do like that.
I was very happy about my work , I always wanted to develop a company which helps people somehow in their daily day-to-day life in solving their problems.
I hate doing job under a boss. I want to be my own boss, so I started following my passion and build an empire of entrepreneurship. I started my journey as a business owner, I started one company named “Febrimetal” at the age of 21 it was an online grocery portal, due to lack of knowledge about websites, funding, business development it failed and I end up with loss. It was not huge loss as that was my first project and investment was very less, that is of $750 that’s all.
After that, I started my You Tube channel in 2016 name ” kare aur sikhe” it was a life-changing decision for me. The main focus of this channel is to help people through Technology, Blogging, Business Development and On line Earning.